I am trying to calculate heating and cooling degree hours for my case study.
As i am trying to simulate and study differences in operative temperature by using different control options, i realize that the results i get are depends in heating and cooling setpoint temperatures that i set in enviromental control.
I set 21-degree for heating setpoint and 26-deggree for cooling setpoint. In case i increase or decrease the setpoint temperatures, the operative temperature of the room fluctuates accordingly.
Do you have any idea what is the right way to take my results?
Forum for DesignBuilder EnergyPlus simulation users to exchange views and questions. Posts regarding use of Detailed HVAC should go to the EnergyPlus HVAC forum
Moderator: DesignBuilder Support
1 post • Page 1 of 1
Who is online
Users browsing this forum: No registered users and 10 guests