The location of inlet and outlet can be specified in CFD, but I was wondering if DB/Energy Plus has the same capability. If not, I was wondering how currently the DB/E+ program determines/considers the location of air inlet and outlet.
Thanks a lot,
Forum for DesignBuilder EnergyPlus simulation users to exchange views and questions. Posts regarding use of Detailed HVAC should go to the EnergyPlus HVAC forum
Moderator: DesignBuilder Support
1 post • Page 1 of 1
Who is online
Users browsing this forum: Google [Bot] and 14 guests